Reinstall the access panel and disconnect block. Turn on the circuit breaker and furnace switch. Then set the thermostat to a lower temperature and wait for the AC to start (see “Be Patient at Startup,” below). The compressor should run and the condenser fan should spin. If the compressor starts but the fan doesn’t, the fan motor is most likely shot. Shut off the power and remove the screws around the condenser cover. Lift the cover and remove the fan blade and motor (photo 7). Reinstall the blade and secure the cover. Then repower the unit and see if the fan starts. If it doesn’t, you’ve given it your best shot—it’s time to call a pro.
A & A Air Conditioning Heating & Sheet Metal is a full-service solar provider serving Grass Valley & surrounding areas. Even if you're just interested in learning more about solar power options, contact our friendly and knowledgeable team today. We'll help you determine what's right for your needs. From skilled installation to high quality service, you know you can trust our team. Our technicians have experience and an attention to detail to ensure your solar energy system is installed and maintained correctly. Give us a call today!
Central home air conditioner service systems consist of two major components: a condensing unit that sits outside your house, and the evaporator coil (often referred to as an A-coil) that sits in the plenum of your furnace or air handler. The refrigerant in the A-coil picks up the heat from your home and moves it to the outdoor condensing unit. The condensing unit fan blows outside air through the condensing coil to remove the heat. The condensing unit houses the three parts replaceable by a DIYer: the contactor, the start/run capacitor(s) and the condenser fan motor. The condensing unit also houses the compressor, but only a pro can replace that. The A-coil has no parts that can be serviced by a DIYer.