We’ve found that many homes and businesses in Atlanta face significant indoor air quality issues as a result of the seasonal high humidity in our area, which creates conditions ripe for mold and mildew growth in both old and new HVAC systems. Our HVAC technicians can help you determine which strategies will work best for neutralizing airborne particulates in your home, which often involves a combination of filtration methods and ultraviolet light technology that together can help keep your system perpetually free of contaminants. We can also install whole-house dehumidifiers and humidifiers, which can make a huge difference in the amount of work your HVAC unit will have to do to be effective.
As a Bryant Factory Authorized Dealer, Welzig Heating & Air consistently performs to strenuous standards of technical competence, business ethics, and customer approval. Our team is NATE-certified, factory trained and regularly updated in progressive technology. Equipped with leading edge equipment, tools, and a full inventory of genuine manufacturer’s replacement parts, we properly size and install new systems, accurately diagnose existing systems, and resolve the majority of issues right then and there.
The contactor (relay) and start/run capacitor(s) (see illustration below) fail most often and are inexpensive. So it’s a safe bet to buy and install those parts right away, especially if your air conditioning service unit is older than five years. The condenser fan motor can also fail, but it runs about $150 — hold off buying that unless you’re sure that’s the culprit.
If you believe that the ac not working or you’re getting little or no cold air, check these three things first. Make sure all the registers in the house are wide open. Then be sure the furnace filter is clean. Then go outside and clean off the condenser coils (Photo 2). If several registers were closed or the filter was clogged, the reduced airflow could have caused the evaporator coil to ice up and stop cooling your home. If you’ve changed the filter and opened all the registers and you’re still not getting airflow at the registers, deice the A-coil. Move the thermostat mode switch from “Cooling” to “Off” and move the fan switch from “Auto” to “On.” Let the blower run for at least 30 minutes or until there’s good airflow at the registers. Then turn the AC back on to test it. If it works for the next 12 hours, you’ve solved the problem.
A Bit Pricy For the Work Done But It Was A Necessary Fix That Required The Tech To Make A Trip To Home Depot And Back. When Calling For The Repair I Expected A Much More Severe Problem That If I Had Been Correct Would Have Been A Much More Expensive Fix. The Problem Turned Out To Be A Simple Problem That Required The Tech To Make A Trip To Home Depot For A $10 Part Afterwhich He Was Able To R&R The Part In About Two Minutes. Problem Solved.
HVAC Repair Co